
Optional Multi Family Service CalculationsThis calculation is the workhorse for all multifamily dwelling units. NEC 220.84 gives the technique repeated here:Determine the total connected load then multiply by the demand factor as given in table 220.84Total connected load is computed as follows:1. 3va per square foot.

Many electrician workbooks and
practice exams are now available
